2-13. OPERATING PROCEDURES- cont.
(8) Allow water to flow into 20K tank until full (refer to applicable TM), then close gate valve S1.
(9) Continue to operate pumping stations until downline water storage and distribution system is full.
Determine chlorine residual and adjust chemical solution level in hypochlorination unit D2 as
required Refer to the applicable TM.
If Installed, open discharge valve on 20K tank Refer to the applicable TM.
Start and operate 125 gpm pump Dl Refer to the applicable TM.
To dispense water though the elbow valves, proceed as follows
(a) Connect elbow valves D4 and D5 to water storage containers.
(b) Open discharge valve D3.
(c) Open elbow valves D4 and D5.
(d) When storage containers are full, close elbow valves D4 and D5 and disconnect from water
(e) Close discharge valve D3
To dispense water through distribution nozzles, proceed as follows.
(a) Open discharge valve D8.
(b) Place distribution nozzles (D6 and D7) in water storage containers and squeeze control handles
to dispense water.
(c) When water storage containers are full, release control handles on distribution nozzles.
(d) Close discharge valve D8.
When water discharge is complete, shutdown 125 gpm pump D1. Refer to the applicable TM).