2-10. ASSEMBLY AND PREPARATION FOR USE cont.
Assemble 4-Inch Hose Connection Kits. Refer to figure 2-23.
To prevent contamination of drinking water, make sure protective caps and plugs are installed
when components are not in use. Do not remove caps and plugs from components until
couplings are ready to be connected.
Install all valves with control handles in upright position and valves fully closed.
Two 4-inch hose connection kits are used in the water system Kit no. 2 is shown, kit no. 1 is
All couplings in this kit are 4 inch diameter.
Connect two 20 foot discharge hoses (2 and 3) to tee (1) (from 2-inch hose connection kit).
Connect tee (4) to 20 foot discharge hose (3) (3) Connect quick acting valve (6) to tee (4).
Connect 20 foot discharge hose (7) to quick acting valve (6).
Connect butterfly valve (8) to 20 foot discharge hose (7).
Unfold nozzle stand assembly (9) and attach butterfly valve (8) to bracket on stand.
Repeat steps 1 through 6 to assemble kit no. 1.
On kit no 1, install cap (5) on open coupling on tee (4).
Prepare 20K Collapsible Water Tanks. Prepare water tanks for use in accordance with the applicable TM.
Prepare 350 Gpm Pumps. Prepare 350 gpm pumps for use in accordance with the applicable TM.
Prepare 125 Gpm Pumps. Prepare 125 gpm pumps for use in accordance with the applicable TM.
Hypochlorination Unit. Prepare hypochlorination unit for use in accordance with the applicable TM.