TM 10-8110-202-13 & P
Section Ill. OPERATION UNDER USUAL CONDITIONS
2-3. FILLING THE DRUM
Services of organizational maintenance should be used for
original unpacking and inspection.
a. Perform preventive maintenance checks and services (PMCS). See Table 2-1.
b. Locate the drum near source of water supply. Choose a site as level and firm as
c. Fully collapse drum as follows:
Take one of the two coupler valves
(1) that come with the drum and
turn its handwheel (2) counterclock-
wise all the way to completely open
the coupler valve.
At one end of the drum remove dust cap (3) from adapter assembly (4).
(3) Slide coupler valve (1) onto adapter assembly (4). Lock coupler valve (1) onto adapter
assembly (4) by pushing in the cam arms (5).