4-15. NOZZLE STAND ASSY/REPAIR
a. Remove stand assy from system by folding up and
replacing with serviceable stand. Ensure cap is on
end of nozzle when hanging on new stand.
Only disassemble the parts of stand that require repair or replacement.
b. With a common screwdriver pry open three s-hooks
(1) on chain ends and remove from sash chains (2) and
legs (3) and (5).
c. Remove two cotter pins (6) from clevis pins (4) in legs
d. Remove pins (6) and separate legs (5) from
upper connection point.