2-9.3.2 Water Storage and Dispensing Tanks. Continue with the water storage and dispensing tank setup
procedures which were begun. Attach hoses and valve and tee assys for tanks 4 through 7 (see page 2-30).
Remember that in every case for tanks 4 through 7, 20-foot hoses will be alternated with 10-foot hoses, and that
hose assy is periodically interrupted with water tank valve and tee assys.
2-9.3.3 350 GPM Pump Connection Kit - Input Flow Side. Perform the following after the hoses and valve
and tee assys for tanks 1 thorugh 7 have been attached, and after the left-hand discharge hose interconnection
kit (indicated by tee assys 14 and 16, page 2-29) have been installed. See TM 5-4320-226-14/24P.
a. Begin at the input flow side of the tanks in the top row. Attach the end of the discharge hose which is
fastened to the valve and tee assy for tank 7 (see page 2-29) to the end of the tee assy (17) (page 2-29) provided
with the 350 GPM pump connection kit. Position these items as shown on page 2-29.