Table 3-1. Operator Troubleshooting (Continued)
TEST OR INSPECTION
3. Collapsible Tank Vent Pipe Leaks.
Step 1. Inspect relief caps, vent pipes and cap screws for looseness, cracks or damaged gaskets.
Torque loose cap screws to 30 inch pounds.
Notify higher maintenance if disassembly is required.
4. Hypochlorination Unit Fails to Perform Per Instruction in Paragraph 2.12.
Step 1. Check unit instruction plate to ensure unit is properly serviced
If unit still malfunctions, notify higher maintenance.
Section III. OPERATOR MAINTENANCE PROCEDURES
Operator maintenance consists of daily inspections when the water distribution system is set up for use,
replacement of water hoses and hose fittings. Replacement of defective units or components is beyond the scope
of operator maintenance and requires the services of organizational maintenance.