TM 5-5430-211-13 & P
Do not pump in more than 50,000 gallons.
Do not let the height at any point exceed 5 feet.
Prop up the inlet and/or outlet coupling with a block of wood if they are straining the fabric.
Do not let the hoses pull on the couplings.
SECTION IV OPERATION UNDER UNUSUAL CONDITIONS
OPERATION IN EXTREME HEAT
The tank will withstand temperatures of up to 50 degrees C (120 degrees F).
Shade the tank with a shield to prolong the life of the tank at these elevated temperatures the water will also
OPERATION IN WINDY CONDITIONS
If only partially filled, the tank may roll over in windy conditions.
Secure the tank with guy ropes if high winds are expected.
Pass the guy ropes under and over the tank and fasten them securely to stakes in the ground.
DO NOT attach the guy ropes to the handles.