Operation Instructions (continued)
During Liquid Storage Inspection
Frequent and regular inspection of tank to detect any evidence of leakage will permit repairs while
damaged area is small in size.
Frequent and regular inspection will prevent the accumulations of debris that may damage the
4.3.1 Attach supply line to tank. Check the vent fitting installation to be sure that the cap is not
plugged then fill to noted capacity.
4.3.2 Observe tank body, fittings, and vent during filling operations to assure that they are secure and
do not leak.
Caution: Do not exceed the noted capacity of the tank when filling.
If metering gauge is not available at the time of filling, do not exceed the
recommended maximum filled height of 5.00 ft.
4.3.3 With all plumbing attached, liquid may be introduced into the container by several means. Two
recommended methods are:
With the standpipe in place and vent relief valve open water may be introduced into
the tank through the filler/discharge fitting until the fluid reaches