Section I. REPAIR PARTS AND SPECIAL TOOLS LIST
COMMON TOOLS AND EQUIPMENT.
For authorized common tools and equipment, refer to the Modified Table of Organization and Equipment (MTOE), CTA
50-970 or CTA 8-100, applicable to your unit.
SPECIAL TOOLS, TMDE AND SUPPORT EQUIPMENT.
Refer to the Maintenance Allocation Chart contained in Appendix B for maintenance tasks authorized at unit level
maintenance and the TMDE and support equipment required to perform these tasks. No special tools are required to
maintain the 800K Water Storage and Distribution System.
Repair parts are listed and illustrated in the repair parts and special tools list, TM10-4610-242-23P, covering unit, direct
support, and general support maintenance of this equipment.
Section II. SERVICE UPON RECEIPT
Transport. The water system is designed to be packaged and shipped inside the twelve tricons supplied
with the system. Transport the water system only on equipment compatible with tricon transport
Site Selection. When selecting a site for installation of the water system, consider the overall operating
area. Siting must include access to the main water source (TWDS), adequate space to set up 16 water
tanks and associated hoses, and space for movement of water transport vehicles (minimum space required
260 x 275 feet). Site should be level and provide good water drainage away from system components. If
possible, site should slope downhill from water source to water dispensing points.
The water system does not require special sheltering during normal operation. Heated shelters are required when
operating in extremely cold conditions (below 32° F). Store unused water system components in the tricons to prevent
damage and minimize routine maintenance.